Sep. 30, 2022
Fire-fighting pipes and fittings are the most basic components of the fire-fighting system, connecting fire-fighting equipment, and delivering fire-fighting water.
Due to special requirements, the thickness and material of fire pipelines have special regulations, and they are sprayed with red paint. Fighting Pipes and Fittings must have the characteristics of pressure resistance, corrosion resistance and high temperature resistance.
Standardized fire piping facilities
As a standardized industrial product, fire pipes and fittings are strictly divided into different specifications. If buyers want to buy suitable products, they must have a clear understanding of these specifications.
Now, let's follow this guide to learn what to look out for when selecting fire pipes and fittings.
Pipe type is an important factor affecting the quality of pipe grooved connections. Most of today's fire pipeline facilities are connected by grooves. For the advantages of grooved connections, you can refer to the following:
The groove connection method is suitable for a wide range of pipeline types. "Technical Regulations for Grooved Connection Pipeline Engineering" (CECS151:2003) points out: "The groove connection method can be used for galvanized welded steel pipes and welded steel pipes, galvanized seamless steel pipes and seamless steel pipes, stainless steel pipes, etc.” However, since the form of the weld has a certain influence on the quality of the steel pipe groove connection, the weld seam of the welded steel pipe is prominent, which is not conducive to the pressure groove of the steel pipe. Therefore, seamless steel pipes should be the first choice during installation and construction, followed by straight seam welded pipes, and spiral welded pipes should be avoided. If it is necessary to use the spiral welded pipe, the corresponding grooved pipe fittings should also be used.
Since the grooved pipe fitting is engaged with the outer wall of the pipe, excessive deviation of the outer diameter of the pipe will cause the pipe to not match the clamp, which will cause the joint to seep. In addition, unqualified pipe material, weak galvanized layer, and insufficient thickness of the pipe wall may cause the pipe to break, the galvanized layer to fall off in large quantities, or the high-frequency weld to crack, which will eventually lead to water seepage or rupture of the joint. Therefore, strict control of pipe quality is essential. All kinds of pipes should comply with the corresponding national standards. For example, galvanized welded steel pipes should meet the requirements of "Galvanized Welded Steel Pipes for Low-Pressure Fluid Transport" (GB/T3091), and seamless steel pipes should comply with "Seamless Steel Pipes for Fluid Transport" ( GB/T8163), the plastic-coated galvanized welded steel pipe and the plastic-coated seamless steel pipe shall meet the requirements of "plastic-coated composite steel pipe for water supply" (CJ/T). In addition, the wall thickness of the steel pipe shall also meet the minimum wall thickness requirements.
Insufficient roundness of the nozzle is an important reason that affects the quality of the pipe groove connection. Before construction, the roundness of incoming pipes should be checked. The inspection can be carried out according to the following methods: Divide the pipe section into 8 equal parts, measure 4 diameters respectively, and compare them with the standard value. Where the roundness is not up to standard pipe sections should be rounded or cut off. The roundness of the pipeline is not up to standard, which is often caused by the collision of the pipeline or the extrusion of the pipes during transportation or loading and unloading. China has good experience in pipe transportation. The engineers and technicians in this country have adopted the method of installing a cross support frame at the pipe end, which has solved the problem of pipeline compression and deformation, which is worth learning and popularizing.
The sealing ring used in the grooved pipe joint realizes the sealing performance of the system by increasing the pressure. From the cross-section, it belongs to the "C" type design. The higher the pressure, the better the sealing performance. The material used for the sealing ring can be determined according to the medium conveyed by the pipeline, and different materials have different letter codes on the sealing ring. For example, EPDM rubber (code E, black) is usually used in fire engineering systems; silicone rubber (code S, the sealing ring material of the pressure cooker, is milky white) for drinking water; Nitrile rubber (code D, orange); natural rubber (code N, black). Therefore, in fire protection projects, black EPDM rubber rings must be used.
Fire fittings with black EPDM seals
Rated working pressure refers to the maximum allowable working pressure of grooved fittings under working conditions, expressed in megapascals (MPa). At present, the rated working pressure of grooved fittings produced by various manufacturers in China is basically the same, namely, Grooved pipe fittings (such as elbows, tees, crosses, etc.) are generally 2.5Mpa; while threaded reducing tees and crosses; threaded mechanical tees and crosses; threaded flanges and other threaded pipe fittings are usually is 1.6MPa. The number of kilograms usually mentioned in engineering refers to the pressure of kilograms per square centimeter. Its code is Kgf/㎝ 2, and its relationship with Mpa is 1Mpa≈10 Kgf/ cm2.
Chinese Standard: Grooved pipe fittings belong to the automatic sprinkler system, design standard GB 5135.11-2006; technical specification GB/T 36019-2018.
International Standard: American Design Standard AWWA C606; International Standard ISO 6182.
Groove connection standard: ASME B36.10, ASTM A53-A53M, ISO4200.
China requires that the material grade should not be lower than QT450-10;
Tensile strength σb (MPa): ≥450
Conditional yield strength σ0.2 (MPa): ≥310
Elongation δ (%): ≥10
Chemical element content: carbon C: 3.70-4.00; Si: 2.15-2.93; Mn: 0.46-0.66; S: 0.010-0.016; P: 0.027-0.07; Mg: 0.027-0.050; Re: 0.026～0.043
I believe that after reading this guide, you already have a certain understanding of fire fighting pipes and fittings.
If you want to know more, please click the link below to enter the official website of Jianzhi Group, where there is more knowledge about fire pipe fittings.
Tel: +86 022 8848 8866
Office In Tianjin:
Heping District, Tianjin, China.
Production Base 1:
Chifeng, Inner Mongolia, China.
Production Base 2:
Tangshan City, Hebei Province, China.
SeoKeywords: Galvanized Pipe Fittings Supplier galvanized pipe fittings manufacturers cheap galvanized pipe fittings galvanized pipe fittings wholesale galvanized pipe fittings Saudi Arabia galvanized pipe fittings canada 1/2 inch galvanized pipe fittings 3 4 galvanized pipe fittings galvanized pipe fittings for sale galvanized pipe fittings price list galvanized pipe fittings size gi pipe fittings price list philippines bulk black pipe fittings black pipe fittings wholesale grooved fittings for fire fighting system grooved pipe fitting Wholesale grooved fittings manufacturer black pipe reducer iron pipe bend galvanized elbow gi elbow price black iron elbows grooved elbow
Get the latest price by sending an email.